The pump requires only little maintenance. However, the following points must be observed.
Connections Of Vacuum Pump
A non-return valve should be installed in the suction line. It prevents back flow of gas and liquid in the suction piping when the pump stopped.
If the pump shall be started-up or stopped with closed shutoff element, e.g. Valve in the suction line, cavitation occurs, too.
The discharge line must not be led more than 1m vertically or diagonally upwards. If a shutoff element is installed in the discharge line behind the liquid separator, it must be ensured that the pump cannot be put into operation while this shutoff element is closed.
Seal Water Line
For a good operation the watering vacuum pumps must be supplied with a seal water which is clean, non abrasive and of any solids. The service seal water should not exceed 30.31 degree centigrade and the gas handled should be maximum 90 degree centigrade.
Country of Origin
Made in India
Developed and Managed by Infocom Network Private Limited.